The SpectrAlert Advance series of notification appliances is designed to simplify installations, with features such as plug in designs, instant feedback messages to ensure correct installation of individual devices, and 11 field-selectable candela settings for wall and ceiling strobes and horn/strobes.
When installing Advance products, first attach a universal mounting plate to a four-inch square, four-inch octagon or double-gang junction box. The two-wire mounting plate attaches to a single-gang junction box.
Next, connect the notification appliance circuit wiring to the SEMS terminals on the mounting plate.
Finally, attach the horn, strobe or horn/strobe to the mounting plate by inserting the product’s tabs in the mounting plate’s grooves. The device will rotate into position, locking the product’s pins into the mounting plate’s terminals. The device will temporarily hold in place with a catch until it is secured with a captured mounting screw.
The SpectrAlert Advance series includes outdoor notification appliances. Outdoor strobes and horn/strobes (two wire and four wire) are available for wall or ceiling. Outdoor horns are available for wall only. All System Sensor outdoor products are rated between minus 40 degrees Fahrenheit and 151 degrees Fahrenheit in wet or dry applications.
1. Full Wave Rectified (FWR) voltage is a non-regulated, time varying power source that is used on some power supply and panel outputs.
2. P, S, PC, and SC products will operate at 12 V nominal only for 15 and 15/75 cd.
Accessories designed for use with this product - To add any of these accessories to your order, simply fill in the quantity you want and click the large "Add to Cart" button above