Altronix ACMS8CB is UL listed sub-assemblies designed to be used in Altronix wall and rack mount enclosures. Input power to ACMS8CB is to be derived from eFlow series power supplies. Dual input design allows power to be steered from two (2) independent low voltage 5 to 24 VDC power sources into eight (8) independently controlled PTC protected outputs. Outputs are activated by an open collector sink, normally open (NO), normally closed (NC) dry trigger input, or wet input from an Access Control System, Card Reader, Keypad, Push Button, PIR, etc. ACMS8CB will route power to a variety of access control hardware devices including Mag Locks, Electric Strikes, Magnetic Door Holders, etc. Outputs will operate in both Fail-Safe and/or Fail-Secure modes. The FACP Interface enables Emergency Egress, Alarm Monitoring, or may be used to trigger other auxiliary devices. The fire alarm disconnect feature is individually selectable for any or all of the eight (8) outputs. The spade connectors allow you to daisy chain power to multiple ACMS8CB modules. This feature allows you to distribute the power over more outputs for larger systems.
Two (2) independent low voltage inputs.
Input 1 and Input 2 voltage range: 5VDC to 24VDC, up to 10A each or 16A total input.
Eight (8) Individually Controlled trigger inputs:
a) Normally open (NO) inputs.
b) Normally closed (NC) inputs.
c) Open collector sink inputs.
d) Wet Input (5VDC - 24VDC) with 10K resistor.
e) Any combination of the above.
PTC protected outputs rated @ 2A per output, Class 2 power-limited. Total output 16A max.
Do not exceed the individual power supply ratings.
Total output current should not exceed max. current rating of the power supplies employed on each input.
Eight (8) selectable 5VDC - 24VDC independently controlled outputs or eight (8) indepently controlled Form “C” relay outputs:
a) Fail-Safe and/or Fail-Secure power outputs.
b) Form “C” relays rated @ 2.5A.
c) Auxiliary power outputs (unswitched).
d) Any combination of the above.
Individual outputs may be set to OFF position for servicing (output jumper set to middle position).
Does not apply to Dry Contact applications.
Any of the eight (8) PTC protected power outputs are selectable to follow power Input 1 or Input 2.
Output voltage of each output is the same as the input voltage of the input selected.
Fire Alarm Disconnect
Fire Alarm disconnect (latching or non-latching) is individually selectable for any or all of the eight (8) outputs.
Fire Alarm disconnect input options:
a) Normally open [NO] or normally closed [NC] dry contact input. Polarity reversal input from FACP signaling circuit.
FACP output relay [NC] contact or provides 10k resistance with [EOL JMP] intact.
PTC are rated 2A each.
Red LEDs indicate outputs are triggered.
Blue LED indicates FACP disconnect is triggered.
Individual voltage LEDs
Operating 0ºC to 49ºC (32ºF to 120ºF).
Storage -20ºC to 70ºC (-4ºF to 158ºF).
Relative Humidity 93% +/-5%.
BTU/Hr. (approx.): 4 BTU/Hr.