Altronix AL1012ULACMJ converts a 115VAC 60Hz input into eight (8) independently controlled 12VDC Fail-Safe and/or Fail-Secure outputs with a total of 10A continuous supply current. These power outputs can be converted to dry form "C" contacts. Outputs are activated by an open collector sink or normally open (NO) dry trigger input from an Access Control System, Card Reader, Keypad, Push Button, PIR, etc. This unit will route power to a variety of access control hardware devices including Mag Locks, Electric Strikes, Magnetic Door Holders, etc. The outputs will operate in both Fail-Safe and/or Fail-Secure modes. This unit is designed to be powered by one common power source (factory installed) which will provide power for both the board operation and locking devices, or two (2) totally independent power sources, one (1) providing power for board operation and the other for lock/accessory power. The FACP Interface enables Emergency Egress, Alarm Monitoring, or may be used to trigger other auxiliary devices. The fire alarm disconnect feature is individually selectable for any or all of the eight (8) outputs.
Fire Alarm disconnect (latching or non-latching) is individually selectable for any or all of the eight (8) outputs.
Fire Alarm disconnect input options:
a) Normally open (NO) or normally closed (NC) dry contact input.
b) Polarity reversal input from FACP signaling circuit.
Alarm output relay indicates that FACP input is triggered (form "C" contact rated @ 1A 28VDC not evaluated by UL).
Short circuit and thermal overload protection.
Red LEDs indicate outputs are triggered (relays energized).
Green LED indicates FACP disconnect is triggered.
AC input and DC output LED indicators.
Built-in charger for sealed lead acid or gel type batteries.
Automatic switch over to stand-by battery when AC fails.
Zero voltage drop when unit switches over to battery backup (AC failure condition).
Battery fail and battery presence supervision (form "C" contact).
Operating 0ºC to 49ºC (32ºF to 120ºF).
Storage - 20ºC to 70ºC ( - 4ºF to 158ºF).
Relative Humidity 85% +/- 5%.
BTU/Hr. (approx.): 61 BTU/Hr.