120VAC 60Hz, 8.0A input.
Power supply input options:
a) Two (2) common power input for either ACM8CB and lock power (factory installed).
b) Two (2) isolated power inputs (external power supply is required), (current is determined by the power supply connected, not to exceed a maximum of 10A total).
Sixteen (16) Access Control System trigger inputs.
a) Sixteen (16) normally open (NO) inputs.
b) Sixteen (16) open collector inputs.
c) Any combination of the above.
12VDC and 24VDC outputs.
Maximum output current Options:
A) 24VDC @ 9.6A plus 12VDC @ 9.3A.
PTC Protected Power-limited Outputs (auto-resettable).
Sixteen (16) independently controlled outputs can be Fail-Safe and/or Fail-Secure power outputs.
Sixteen (16) auxiliary power outputs (unswitched) (outputs are rated 2.5A).
Filtered and electronically regulated outputs (built-in power supply).
Thermal and short circuit protection with auto reset.
Power Supply input fuse ratings:
eFlow104NB - 6.3A/250V
eFlow102NB - 5A/250V
ACM8CB boards' main fuse is rated at 10A PTC outputs are rated @ 2.5A each.
AC fail supervision (form "C" contacts).
The notification trigger is selectable for 30 seconds (factory set) or 2 hours.
Battery fail and presence supervision (form "C" contacts).
Low power shutdown. Shuts down DC output terminals if battery voltage drops below 71-73% for 12V units and 70-75% for 24V units (depending on the power supply). Prevents deep battery discharge.
Fire Alarm disconnect (latching or non-latching) is individually selectable for any or all of the sixteen (16) outputs.
Fire Alarm disconnect input options:
a) Normally open (NO) or normally closed (NC) dry contact input.
b) Polarity reversal input from FACP signaling circuit.
Alarm output relay indicates that FACP input is triggered (form "C" contact rated @ 1A 28VDC).
Built-in charger for sealed lead acid or gel type batteries.
Automatic switch over to stand-by battery when AC fails.
Zero voltage drop when unit switches over to battery backup (AC failure condition).
Red LEDs indicate outputs are triggered (relays energized).
Green LED indicates FACP disconnect is triggered.
AC input and DC output LED indicators.
Operating: 0° C to 49° C (32° F to 120° F).
Storage: - 20° C to 70° C ( - 4° F to 158° F).
Relative Humidity 85% +/- 5%.
BTU/Hr (approx.): 177 BTU/Hr.
System AC input VA requirement: 960VA