INTELLIGENT SENSING TECHNOLOGY™
Microprocessor controlled -reduces the number of non-emergency or unwanted alarms.
LATCHING ALARM INDICATION
Microprocessor controlled -Automatically identifies initiating alarm, even after alarm condition has subsided.
Interconnectable to both BRK Smoke and CO Alarms
TWO SILENCE FEATURES
Can silence the low battery chirp for up to eight hours or temporarily silence an unwanted alarm.
The BRK Electronics® Cat. No. CO5120BN is a wire-in, 120 VAC/DC, 60Hz with 9V battery backup single and/or multiple station carbon monoxide alarm specifically designed for residential and institutional applications including sleeping rooms of hospitals, hotels, motels, dormitories and other multi-family dwellings. Model CO5120BN complies with UL2034, NFPA720, HUD, FHA and other agencies that model their codes after the above agencies. It meets building codes where AC/DC carbon monoxide alarms are required.
BRK Electronics® CO5120BN features a permanently installed CO sensor, Intelligent Sensing TechnologyTM for fewer unwanted alarms, an 85dB horn, a 9V battery backup power supply, an easy access side-load battery drawer, two silence features: unwanted alarms and low battery silence and is interconnectable with up to 18 devices including both BRK Smoke and CO Alarms. The "Smart Interconnect" feature allows the unit to be interconnected to BRK smoke alarms. If there is a smoke event, the CO5120BN horn pattern will emit the same sound as a smoke alarm, that is 3 beeps, pause, 3 beeps, pause. If there is a CO event, the interconnected CO alarms will sound with their normal horn pattern. The unit features "Latching Alarm Indication". When interconnected in series, the unit that triggered the alarm rapidly flashes its red LED indicator. After the alarm condition subsides, the initiating unit will store in memory or "latch" the information and begin to flash once every 5 seconds. The red LED indicators remain off on all other interconnected units. The unit mounts to any standard 4" junction box. Keyhole slots in the mounting bracket eliminate the need to remove the junction box screws for installation. Battery installation and removal can occur while the unit is mounted to the ceiling or wall via the side load battery compartment. Two locking features are provided to discourage battery theft and/or theft of the unit. Connection to AC power is made with a "Quick-Connect" wiring harness. Installation is quick, easy and cost effective.