DUE TO COMPONENT SHORTAGES THERE IS A 12-WEEK LEAD TIME
Self-Aligning Reflective BeamThe Fireray 5000 System is an auto-aligning infrared beam smoke detector. Once the detector head is installed, using the easyfit mounting system, an integral LASER can be activated. This allows the reflective prism to be located quickly and with confidence.
The AutOptimiser beam alignment system then takes over and automatically steers and maintains the beam in the optimum position for reliable performance. The signal generated in the transmitter element and reflected by the prism back to the receiver element is analyzed for the presence of smoke. The internal microprocessor determines an alarm condition when a predetermined level of obscuration is reached.
The system is designed to be mounted so the beam will project between 1ft. (0.31m) and 2ft. (0.61m) below and parallel to the ceiling. Lateral detection may be up to 30ft. (9.144m) on either side of the beam, providing a maximum total coverage area of up to 19,800 square feet (60ft. x 330ft. or 18.29m x 100m).
(1) Prism included for 15-160 foot installations. (4) Prisms required for 160-330 foot installations.Use the FE-5000-004 Long Range Kit
The projected beam type smoke detector shall be listed to U.L. 268 and shall consist of up to four integrated transmitter, receiver detector heads and single low level remote control unit. The detector shall operate between a range of 26.25 ft. to 330 ft. (8m to Fireray 5000 Reflective Beam Smoke Detector 100m). The temperature range of the system shall be -4°F to 131°F (-20°C to 55°C). The beam detector heads shall include an integral built-in laser pointer to assist prism mounting. The beam detector shall feature automatic gain control which will compensate for gradual signal deterioration from dirt accumulation on the lenses. The beams detector heads shall include AutoOptimise Self-Correcting motorized head feature to ensure unit is always receiving maximum signal available, and shall automatically compensate for Building Shift. The unit shall include a low level remote display and control unit with LCD readout for set-up, reporting and testing of up to 4 separate detector heads.
Manufactured by Fire Fighting Enterprises